Capacitance switch can control the level and upper and lower limit of bulk, granular, powder, and liquid material silos; Widely used in metallurgy, petroleum, chemical industry, light industry, coal, cement, grain, and other industries.
Nowadays, capacitance switches have been widely used, so the variable types could have various installation methods and specifications from different level switch suppliers. Here we have the following notes for FEEJOY
The level switch is usually installed on the sidewall of the warehouse body by side installation (installed on the side of the warehouse wall), and the height of the material level is detected at the upper and lower limit positions. Top installation) method.
The threaded installation tube should be as short as possible during side mounting so that the end of the probe thread is flush with the inner wall of the groove to avoid material accumulation at the root.
The distance between the electrode and the silo wall should be greater than 200mm during top-loading, and the position that can avoid the impact of materials during feeding should be selected.
When the warehouse wall is made of concrete, the shell of the level switch should be connected to the steel bar reliably. When the warehouse wall is made of non-metal, an auxiliary probe should be installed.
When measuring solid powder or block material with a large specific gravity, the probe should be fixed to prevent the pusher pole on the material side from deviating from the normal position. For measuring liquids, if there is a stirring device, the cable probe should also be fixed.
When the user disassembles and assembles the level switch, it is forbidden to hold the case by hand and twist it. Use a wrench to turn the hexagon bolt.
The probe length of the level switch is selected between 100-2000mm, which is a rod probe. The cable probe can be used when the probe length exceeds 2000mm.
When used to detect materials with dielectric constant such as plastic, the probe length should not be shorter than 500mm. Non-metallic silos or materials with dielectric constant ≤1.8 need to add auxiliary probe.
When there is high-power equipment on site, 24VDC power supply should be selected as much as possible.
Due to the use of "one-key calibration" technology, it solves the problem of long-term calibration of capacitive level limit switches in use.
Feejoy's capacitance level switch can control the liquid level and upper and lower limits of bulk, granular, powdery and liquid material silo, and is widely used in metallurgy, petroleum, chemical, light industry, coal, cement, grain and other industries.